If you have a Holman 4/6/9 controller and the display looks ok, but it doesn’t seem to be working then the first thing to check out is whether the rain sensor display says ‘rain sensor wet’ or ‘rain sensor dry’.
If it displays a ‘wet’ message then it means that there is no 24v power going to the controller and therefore no power to operate solenoids.
There are a few things that could cause this:
1) check your RCDs in your meter box as if one of these has tripped then you won’t have power to the box.
2) check your fuse. Most likely a fault will have blown the fuse.
3) It may be that the transformer that converts 240V to 24V has died. Not much you can do here but replace the unit.
But before you call someone out do the ‘wet/dry’ check first!
Some jobs are more fun than others!
The location of this one made it a very enjoyable one, as well as some very generous people who brought us chocolate, drinks and ice cream throughout the day.
It turned out to be a much longer, trickier job than we first imagined, but the result was a good one. Some fresh Sir Walter Buffalo laid and the sprinklers working well.
I went to a job today where the client told me that they were on a shared bore and that only one of their stations would come on. The pump would come on when the rear lawn was running but not on the other 3 stations… strange…
What was going on?
When I got there I also discovered that he had installed a new control box and wired it up himself. I assumed all this was done correctly, but after half an hour of testing various things it dawned on me that what he had done was wire the master/pump wire incorrectly.
He had mistakenly put the pump wire in station 4 and station 4 wire in the pump terminal thus meaning only one station would work. Once we reversed the wires everything worked as it should have.
The learning here is:
- always get the wires back in the right place
- if in doubt make sure you get the pump/MV and common correct. The rest is easy.
And if you ever re-wire your own control box and have just one station come on then consider that you have got the MV/pump wire in the wrong terminal.
Its easy to do!
Last week we did a complete revamp of a front and back yard in Quinns Rocks.
Here are some images of the retic and turf going in. It was Sir Walter Buffalo.
Trenching the easy way
Sir Walter Turf
Compacting to complete the job
Sometimes its possible for us to give you a very accurate quote on your retic and turf needs without viewing the site.
Ideally we would come and check it out with you and discuss your needs, but in the first instance we can look at your home on www.nearmap.com and talk with you on the phone about what is required.
If you are happy with the ball park figures then we can meet you and discuss things more fully.
Most nearmap images are up to date to within around a month and can be used to give a good guide to what work is required. We work anywhere from Two Rocks down to Scarborough and would be happy to quote on your needs.